<?php
/*
 * voltages for raspberry pi
 * requires snmp extend agent script from librenms-agent
 */
$sensor_type = "rasbperry_volts";
$oid = '.1.3.6.1.4.1.8072.1.3.2.4.1.2.9.114.97.115.112.98.101.114.114.121.';
for ($volt = 2; $volt < 6; $volt++) {
    switch ($volt) {
        case "2":
            $descr = "Core";
            break;
        case "3":
            $descr = "SDRAMc";
            break;
        case "4":
            $descr = "SDRAMi";
            break;
        case "5":
            $descr = "SDRAMp";
            break;
    }
    $value = current($pre_cache['raspberry_pi_sensors']["raspberry.".$volt]);
    if (is_numeric($value)) {
        discover_sensor($valid['sensor'], 'voltage', $device, $oid.$volt, $volt, $sensor_type, $descr, '1', '1', null, null, null, null, $value);
    } else {
        break;
    }
}

$oids = snmp_walk($device, '.1.3.6.1.4.1.10876.2.1.1.1.1.3', '-OsqnU', 'SUPERMICRO-HEALTH-MIB');
d_echo($oids."\n");

$oids = trim($oids);
if ($oids) {
    echo 'Supermicro ';
}

$type    = 'supermicro';
$divisor = '1000';
foreach (explode("\n", $oids) as $data) {
    $data = trim($data);
    if ($data) {
        list($oid,$kind) = explode(' ', $data);
        $split_oid       = explode('.', $oid);
        $index           = $split_oid[(count($split_oid) - 1)];
        if ($kind == 1) {
            $volt_oid     = '.1.3.6.1.4.1.10876.2.1.1.1.1.4.'.$index;
            $descr_oid    = '.1.3.6.1.4.1.10876.2.1.1.1.1.2.'.$index;
            $monitor_oid  = '.1.3.6.1.4.1.10876.2.1.1.1.1.10.'.$index;
            $limit_oid    = '.1.3.6.1.4.1.10876.2.1.1.1.1.5.'.$index;
            $lowlimit_oid = '.1.3.6.1.4.1.10876.2.1.1.1.1.6.'.$index;

            $descr    = snmp_get($device, $descr_oid, '-Oqv', 'SUPERMICRO-HEALTH-MIB');
            $current  = (snmp_get($device, $volt_oid, '-Oqv', 'SUPERMICRO-HEALTH-MIB') / $divisor);
            $limit    = (snmp_get($device, $limit_oid, '-Oqv', 'SUPERMICRO-HEALTH-MIB') / $divisor);
            $lowlimit = (snmp_get($device, $lowlimit_oid, '-Oqv', 'SUPERMICRO-HEALTH-MIB') / $divisor);
            $monitor  = snmp_get($device, $monitor_oid, '-Oqv', 'SUPERMICRO-HEALTH-MIB');
            $descr    = trim(str_ireplace('Voltage', '', $descr));

            if ($monitor == 'true') {
                discover_sensor($valid['sensor'], 'voltage', $device, $volt_oid, $index, $type, $descr, $divisor, '1', $lowlimit, null, null, $limit, $current);
            }
        }
    }//end if
}

if (preg_match("/(Linux).+(ntc)/", $device['sysDescr'])) {
    $sensor_type = "chip_volts";
    $oid = '.1.3.6.1.4.1.8072.1.3.2.4.1.2.10.112.111.119.101.114.45.115.116.97.';
    $lowlimit     = 3.8;
    $lowwarnlimit = 3.8;
    $warnlimit    = 6.3;
    $limit        = 6.3;
    $descr = 'AC IN voltage';
    $index = '116.2';
    $value = snmp_get($device, $oid.$index, '-Oqv');
    discover_sensor($valid['sensor'], 'voltage', $device, $oid.$index, $index, $sensor_type, $descr, '1', '1', $lowlimit, $lowwarnlimit, $warnlimit, $limit, $value);
    $descr = 'VBUS voltage';
    $index = '116.4';
    $value = snmp_get($device, $oid.$index, '-Oqv');
    discover_sensor($valid['sensor'], 'voltage', $device, $oid.$index, $index, $sensor_type, $descr, '1', '1', $lowlimit, $lowwarnlimit, $warnlimit, $limit, $value);
    $lowlimit     = 2.75;
    $lowwarnlimit = 2.8;
    $warnlimit    = 4.2;
    $limit        = 4.2;
    $descr = 'Battery voltage';
    $index = '116.6';
    $value = snmp_get($device, $oid.$index, '-Oqv');
    discover_sensor($valid['sensor'], 'voltage', $device, $oid.$index, $index, $sensor_type, $descr, '1', '1', $lowlimit, $lowwarnlimit, $warnlimit, $limit, $value);
}

$oids = '.1.3.6.1.4.1.8072.1.3.2.4.1.2.7.117.112.115.45.110.117.116.4';
$value = snmp_get($device, $oids, '-Osqnv');

if (!empty($value)) {
    $type = 'ups-nut';
    $index = 4;
    $limit = 60;
    $lowlimit = 0;
    $lowwarnlimit = 0;
    $descr = 'Battery Voltage';

    discover_sensor($valid['sensor'], 'ups_nut', $device, $oids, $index, $type, $descr, 1, 1, $lowlimit, $lowwarnlimit, null, $limit, $value);
}
unset($oids);

$oids = '.1.3.6.1.4.1.8072.1.3.2.4.1.2.7.117.112.115.45.110.117.116.5';
$value = snmp_get($device, $oids, '-Osqnv');

if (!empty($value)) {
    $type = 'ups-nut';
    $index = 5;
    $limit = 60;
    $lowlimit = 0;
    $lowwarnlimit = 0;
    $descr = 'Battery Nominal';

    discover_sensor($valid['sensor'], 'ups_nut', $device, $oids, $index, $type, $descr, 1, 1, $lowlimit, $lowwarnlimit, null, $limit, $value);
}
unset($oids);

$oids = '.1.3.6.1.4.1.8072.1.3.2.4.1.2.7.117.112.115.45.110.117.116.6';
$value = snmp_get($device, $oids, '-Osqnv');

if (!empty($value)) {
    $type = 'ups-nut';
    $index = 6;
    $limit = 0;
    $lowlimit = 0;
    $lowwarnlimit = 0;
    $descr = 'Line Nominal';

    discover_sensor($valid['sensor'], 'ups_nut', $device, $oids, $index, $type, $descr, 1, 1, $lowlimit, $lowwarnlimit, null, $limit, $value);
}
unset($oids);

$oids = '.1.3.6.1.4.1.8072.1.3.2.4.1.2.7.117.112.115.45.110.117.116.7';
$value = snmp_get($device, $oids, '-Osqnv');

if (!empty($value)) {
    $type = 'ups-nut';
    $index = 7;
    $limit = 280;
    $lowlimit = 200;
    $lowwarnlimit = 0;
    $descr = 'Input Voltage';

    discover_sensor($valid['sensor'], 'ups_nut', $device, $oids, $index, $type, $descr, 1, 1, $lowlimit, $lowwarnlimit, null, $limit, $value);
}
